Switchgear, DC power operated breakers and alarm systems can be some of the most demanding of critical power applications. UPS Rental Utility Trailers are designed to provide uninterruptible power to electrical switchgear, DC control systems, industrial manufacturing and utility applications where continuous duty DC power is a must.
This mobile powerhouse is equipped with battery chargers, batteries, ac and dc meters and controls, external power connections and ancillary safety equipment.
The custom engineered 130VDC trailer accepts either a 3-phase 480VAC or 208VAC input. Input wiring options are available for 50A or 100A at 480VAC. 100A or 150A at 208VAC are also available. With an estimated run time of up to 90 minutes at 400ADC, this trailer outputs 130VDC and can be equipped with 6 strings of VRLA batteries.
Designed to carry continuous and intermittent loads at the maximum rated output, utility
trailers also feature a compact design allowing for uninterruptible power in small spaces and are an excellent option for NERC compliance testing, emergency backup and substation maintenance.
UPS Rental’s staff of field service technicians are on 24x7x365 call to meet our customers’ demands. Whether our customers need an emergency UPS trailer rental or standalone unit, our team is ready to respond.
|Applications:||Switchgear and Utility Markets|
|Total Length:||19.5’L x 8.6’W x 9.7’H|
|Total Weight – Trailer and Contents:||8,400 lbs.|
|Charger Manufacturer:||Hindle Power Systems|
|Charger Output Voltage:||130 VDC|
|Charger Output Current:||100 ADC|
|Input Wiring:||Appleton Connector with Cables (Supplied)|
3W + Ground at 480 VAC or 4W + Ground at 208 VAC
480 VAC or 208 VAC, 3 Ø
100 Amps at 480 VAC or 150 Amps at 208 VAC
|Output Wiring:||2-Wire + Ground|
400 Amps Maximum Output Capacity
4/0 Flexible Cam-Lok Cables to Output Panel
|UPS Battery Information|
|Battery Type:||EnerSys 12VDC, Monobloc, VRLA, Non-Spillable|
|Battery Watts Per Cell:||540 WPC|
|Nominal DC Link Voltage:||120 VDC|
|Number of Cells Per String:||60 Cells|
|Number of Strings:||4 Strings|
|Estimated Battery Run-Time:||60.0 minutes at 400 ADC|
|Battery Disconnect:||400 Amps|
|Number of A/C Units:||1|
|Capacity (Redundant):||1 Ton|
|Total Tonnage:||1 Ton|
|HVAC Supervision | Ambient Temperature | Discrete UPS Alarms|
Cellular Alarm Monitoring